In Phone Numbers, when UCM/GSM4 is in the systrem, the Phone Permission checkboxes are missing for each user. They are enabled by default for all users
KNX/Logic send text to id=01 (self) was invalid. This allows Status on bottom left to work
Divide action Parameters are fixed
In the Zones screen when the "Status " checkbox is checked to show the real time state of zones, when a zone state changes, the screen goes back to the top so higher numbered zones could not be seen easily. Now this has been improved so the zones screen does not jump when any zone state changes.
IRIO 0-10V Dimmer Input switch added parameters "Direction" and "Quick Press" so that the switch can be used to dim up and dim down by long opress
IRIO analog outputs 0-10V added mapped on/off flag which turn off when the analog output value is 0 and turn on value is > 0. This flag controls an output which can be used to switch the analog output on or off
UCM/Cbus2 : When Imported from CBZ, the Register assignment is not changed in Comfigurator if already mapped to Comfort Counter, Flag, Virtual Input etc. If a new Group address is imported, it is Unassigned (ie FF)
Register Monitor Window. This is a new window that allows selected Inputs, Outputs, Counters, Flags, and Sensors to be monitored for real time value. However, an issue is that new file will also ask to log in, even when there is no register defined.
UCM/GSM4 added new 4G type 3 = 7600-LTE to support future LTE module
The new Register Monitor feature is very useful when you want to monitor a range of Comfort registers; Zones/Inputs, Outputs, Counters, Flags, and Sensors. Before this, you had to go to Zones to monitor zones, Outputs to monitor outputs, Counters to monitor counters, etc. This new feature allows all required registers to be monitored in a single window.
Go to Comfort Registers > Register Window.
The Login window appears. Enter a valid user code.
A new window appears "Add Register to Monitor"
Select Counter, Flag, Output, Sensor or ZoneThen select the register number according to the register type selected
Continue adding registers to the monitor window.